FC 35B Insert
User Manual: fc-35b Signal Conditioner Inserts and Manuals - AutomationDirect
Open the PDF directly: View PDF .
Page Count: 2
|Open PDF In Browser||View PDF|
FC-35B Unipolar Voltage or Current to Bipolar Voltage Signal Conditioner inches [mm] General Specifications Surrounding Air Temperature Product Guide Dimensions Specifications (continued) 0 to 60°C (32 to 140°F) IEC 60068-2-14 (Test Nb, Thermal Shock) -20 to 70°C (-4 to 158°F) 3505 HUTCHINSON ROAD CUMMING, GA 30040-5860 Description: The FC-35B is a DIN-rail or side-mount, selectable unipolar input to bipolar output signal conditioner with isolation between input and output, and isolation between 24-volt power and input/output. The FC-35B field configurable isolated signal conditioner is useful in eliminating ground loops and interfacing sensors to PLC analog input modules. It translates unipolar voltage inputs or current inputs to bipolar voltage outputs. The input and output signal levels are selected via DIP switches. In addition, the outputs can be either a direct conversion of the inputs or an inversion (a reverse acting operation). The user also has the option of customizing the input OFFSET (zero) and SPAN (full scale) adjustments that can be set to a percentage of the full scale via a pushbutton on the front panel. Storage Temperature IEC 60068-2-1 (Test Ab, Cold) IEC 60068-2-2 (Test Bb, Dry Heat) IEC 60068-2-14 (Test Na, Thermal Shock) Humidity Environmental Air Vibration Shock Insulation Resistance Version: Rev. A September, 2014 5 to 95% (non-condensing) IEC 60068-2-30 (Test Db, Damp Heat) No corrosive gases permitted (EN61131-2 pollution degree 1) MIL STD 810C 514.2 IEC 60068-2-6 (Test Fc) MIL STD 810C 516.2 IEC 60068-2-27 (Test Ea) >10M @ 500 VDC NEMA ICS3-304 IEC 61000-4-2 (ESD) Noise Immunity IEC 61000-4-3 (RFI) Input Specifications Input Impedance 0-5V, 0-10V, 0-20 mA, 4-20 mA (DIP Switch Selectable/Invertable) 410 kilohm voltage input, 250 ohm current input Protection Type, Component Polarity Protection Diode External DC Power Required 24 VDC ±10%, 40 mA, Class 2 User Calibration Range OFFSET (zero): 0-20% (e.g. 0-1.0V / 5V mode) Weight Load Impedance Sample Duration Time Maximum Inaccuracy Accuracy vs. Temperature Output Current 0.3lbs Wiring Connections Isolation 1800 VDC Power to Output D 1800 VDC Input to Output *applied for 1 second (100% tested) SPAN (full-scale): 80-102% (e.g. 4.0 - 5.1V / 5V mode) 2kilohm Minimum 10 ms 0.1% FSO @ 25°C (1.0% 50 mV / 100 mV) Agency Approvals UL508*, File Number: E157382, CE Number of Positions Wire Range Screw Torque I+ Input Signals Removable Screw Type Terminal Block 2 (Dinkle: EC350V-02P), 3 (Dinkle: EC350V-03P), 6 (Dinkle: EC350V-06P) 28-14 AWG solid or stranded conductor; wire strip length 1/4” (6-7mm) 1.7 inch-pounds (0.19 Nm) Current In DIAG * In order to comply with UL508 Class 2 standards the supplied power must be less than 26 VDC and fused at a maximum of 3 amps. CAL 24V Power 0V mA V INPU PROGRAM MODE SW 8 = 1 FACTORY DEFAU HOLD 10 SEC POWER + 24V ± 10 40mA CLASS 2 ±mV COM ±5V Output Signals ±10V ±15V COM Common NOTE: V+ and I+ must be jumpered for Current input COM ±60 PPM of Full Scale/ °C Maximum ±50 mV/±100 mV @ 2.5mA max, ±5V, ±10V, ±15V @ 7.5mA max Voltage In V+ COM FC-35B V+ ±50 mV, ±100 mV, ±5V, ±10V, ±15V Description I+ Terminal Block Specifications Field Wiring Input Terminal Block Faceplate Label 1800 VDC Power to Input Output Specifications Output Ranges IEC 61000-4-4 (FTB) RFI, (145 MHz, 440 MHz 5W @ 15 cm) Specifications Input Ranges Impulse 1000V @ 1µS pulse OUTPUT External Power Terminal Block Faceplate Label 24 V I Description 24 VDC ±10% (Class 2) 0V 0V Output Terminal Block Faceplate Label Description ±mV ±50 mV or ±100 mV Output COM (used with mV signals) COM Connection ±5V Output ±5V ±10 V Output ±10V ±15 V Output ±15V COM Connection (used with non-mV signals) COM Switch/LED Labels Faceplate Label DIAG CAL Description Diagnostic LED flashing indication Push button switch input to initiate calibration, etc. P.1 Typical Application #1 Status Indicators DIP Switch Settings DIAGNOSTIC LED DIP Switches Located Under Cover FC-35B DC Motor Drive 4-20 mA IN to ±10 V OUT V+ CALIBRATION BUTTON I+ COM DIAG mA Status Indicators FC-35B V INPUT 8 7 6 5 4 3 2 1 PROGRAM MODE SW 8 = 1 FACTORY DEFAULT HOLD 10 SEC POWER + 24V ± 10% 40mA CLASS 2 INVERT INPUTS SW 4 = 1 Indicator SIGNAL CONDITIONER ISOLATED V OR mA INPUT BIPOLAR V OUTPUT INPUTS 0-5 V 0-10 V 0-20 mA 4-20 mA 1 1 0 1 0 2 1 1 0 0 3 1 0 1 1 OUTPUTS ±50 mV ±100 mV ±5 V ±10 V ±15 V 5 1 0 1 0 1 6 1 1 0 0 1 7 1 1 1 1 0 Status Normal Operation Diagnostic LED Calibration OUTPUT CAL Description The Diagnostic LED blinks at a proportional rate to the selected input signal level. This indicates that the unit is operational and functioning within spec. When performing field calibration or a restore to the factory calibration, the LED is used for indication of the internal calibration process and will provide feedback (as described under “User OFFSET and SPAN Calibration) to the user if they have selected an invalid input range. 24V 0V ±mV COM ±5V ±10V ±15V COM 0 1 User OFFSET and SPAN Calibration Input Ranges Application adjustments to calibrate the input signal level: DIP Switch - 1, 2, 3 1 2 0-10 V 0 1 0 4-20 mA 0 0 1 0-5V 1 0-20 mA Output Ranges 1 6 7 0 1 1 1 ±5V 1 1 1 0 1 DIP Switch - 4, 8 1 0 0 ±15 V 1 5 ±50 mV ±10 V 1 0 DIP Switch - 5, 6, 7 ±100 mV 3 1 1 1 0 Input Connection Options 4 8 Calibration Enable 0 1 Invert Acting 1 0 1) Select the input and output signal modes via the dipswitches. 2) Connect 24 volt power to the signal conditioner. 3) Connect the minimum (OFFSET) input signal level desired. 4) Move Switch 8 “CAL EN” to ON, press and hold the CAL pushbutton and release after approximately 3 seconds. The DIAG LED comes ON steady once pressed. If the pushbutton is held >3 seconds, the LED will turn off indiating the User Cal feature is no longer available. The unit returns to normal processing of input data and another press needs to occur to recapture the input minimum value if a User Cal is desired. If the pushbutton is released in <3 seconds, the minimum input value will not be captured and another press needs to occur. If the push button is pressed longer than 10 seconds, the unit will go into “Restore Factory Cal” mode. 5) If the input is within the user calibration, once the pushbutton is released at 3 seconds, the LED will flash 2-3 times. If the input is out of range, the LED will flash several times rapidly. If the out of range occurs, the input needs to be adjusted to the allowable range. In order to remove the User Cal, press and hold the pushbutton for > 10 seconds. 6) Move the Switch 8 “Cal En” to OFF. Connect the maximum (SPAN) input signal level desired and repeat steps 4 and 5. 7) Move Switch 8 “CAL EN” to OFF. Typical Application #2 4-20 mA IN to ±10V OUT Restore Factory Calibration 1) Move switch 8 “CAL EN” to ON, press and hold CAL pushbutton. Once the push button is held and released after 10 seconds, the LED will flash several times indicating a valid restore has taken place. The unit has now been returned to factory calibration. If the push button is released before the 10 seconds has expired, the press will be ignored and go back to regular signal processing based on previous calibration coefficients. 2) Move Switch 8 “CAL EN” to OFF. 3) Start conversion with no power cycle required. P.2
Source Exif Data:
File Type : PDF File Type Extension : pdf MIME Type : application/pdf PDF Version : 1.4 Linearized : No Page Count : 2 Creator : QuarkXPress(R) 7.5 Producer : QuarkXPress(R) 7.5 X Press Private : %%DocumentProcessColors: Cyan Magenta Yellow Black.%%EndComments Create Date : 2014:09:03 09:10:04 Modify Date : 2014:09:03 09:10:04 Title : FC-35B InsertEXIF Metadata provided by EXIF.tools